Question about Coleman Electrical Supplies
Hello, Has this generator been setting for awhile or was it in use when the power ever came back on? Have you tried to repolarize it? To do this , Shut off the generator and unplug any cords or wiring from unit. Take a electrical cord that has a plug on one end and seperate the wires on the other end of cord. Strip the ends of the wire back about half an inch on each seperated wire.Plug the Male end of the wire into one of the 110V recepticles. Connect one of the ends of the wire you stripped back to the positive side of a 12 volt battery. Now with the other end of the wire you stripped back touch it to the Negative side of the battery for 1 sec and remove it. Unplug the wire from the recepticle and battery. Fire up the Generator and check the voltage! This repolarizes the unit and fixes most non generating problems from Non use and back feeding! Hope that helped! Rick
Posted on Jul 02, 2009
Check the voltage regulator. Inspect for any burned spots or a blown fuse.
Posted on Jun 30, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 20, 2016 | Electrical Supplies
Jan 13, 2016 | Coleman Electrical Supplies
Sep 23, 2015 | Honda 3000 Watt Portable Generator
Apr 05, 2010 | Coleman Powermate Premium Plus 6250W...
Mar 16, 2010 | Pramac Electrical Supplies
Oct 03, 2009 | Electrical Supplies
Jul 10, 2009 | Electrical Supplies
Jul 01, 2009 | Northstar Generator 9 Hp, 5500 Watt,...
May 18, 2009 | Watts Onan Portable Generator - 4000 ,...
199 people viewed this question
Usually answered in minutes!