Question about Heating & Cooling
I live in south texas overnight the ac stopped working. The fan is blowing inside but the pump outside does not and the motor attached to the fan is hot? What do i do?
How do you wire a new fan motor? If i open the motor casing to attach the wires what tricks is there to the job?
Posted on Aug 22, 2010
Is the condenser fan (outside) turning? You mention that it's hot but don't say if it's turning or not.
These fan motors normally run pretty hot, but not so much that they shut down due to internal thermal overload protectors.
Both the compressor and the fan have termperature overload protectors to keep them from burning out the motor in the event of an overheated condition. The condenser fan must be running or high freon pressure will put an excessive load on the compressor and it will 'kick out' the high-temp overload protector.
Turn off the unit by pulling the outside disconnect (in a small box near the outside compressor unit) or flip the AC breakers in the breaker box. Wait about 30 minutes for the unit to cool off and turn it back on. If the compressor and fan both run for awhile then kick back off, or the fan motor seems to be working under excessive strain, you've probably got a bad motor start condenser (inside the unit) that little round can that is connected through the fan motor wiring. If it's swollen or leaking, it's almost surely defective and even if it's not, excessive load on the motor is a classic sign of a bad start condenser.
You can usually find these at electrical supply stores, well-stocked hardware stores, or most certainly at an HVAC parts house. Be sure to replace the old one with one of the EXACT same value (in voltage and Microfarads (mF) capacity. The shape may be a little different, but as long as the electrical characteristics are the same and is rated at the same or higher voltage than the original, it will work.
Connect the new condenser, mount it to the frame, and restart the unit. This should take care of the problem.
Hope this helps.
Posted on Jun 28, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Apr 07, 2010 | Goodman CKL24AR24 Air Conditioner
Nov 21, 2008 | Goodman GMS90703BXA Heater
Jun 18, 2018 | Heating & Cooling
251 people viewed this question
Usually answered in minutes!