Question about Heating & Cooling
Had a bad compressor (open motor windings) replaced and now refuses to pump both sides seem equalized at about 105 psi and rise 5-7 psi regardless of the reversing valve being energized or unit running in heat or cool mode.
Sounds like reversing valve is stuck or metering device or check valve is stuck open. If it is a scroll compressor on 3 phase you may need to reverse 2 motor leads. try tapping reversing valve with rubber mallet when running. This may have done in last compressor by sending discharge gas to suction side.
Posted on Jun 28, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Sep 02, 2011 | Goodman CKL24AR24 Air Conditioner
Mar 05, 2011 | Goodman Heating & Cooling
Jul 26, 2010 | Goodman CKL42AR42 Air Conditioner
May 04, 2010 | Goodman CLQ36AR49 Air Conditioner
Jun 23, 2009 | Goodman CLQ36AR49 Air Conditioner
Apr 27, 2009 | Goodman CLQ36AR49 Air Conditioner
Dec 19, 2008 | Goodman CLQ36AR49 Air Conditioner
Jul 10, 2008 | Goodman Heating & Cooling
Apr 07, 2008 | Heating & Cooling
835 people viewed this question
Usually answered in minutes!