Question about Hayward H Series Millivolt 250,000 Btu Pool Heater H2501
Put a new thermocouple in and it still goes out. has a good blue flame when button is depressed but et go of the button and the flame dies
A short circuit in the heater wire will cause an immediate loss of all flame, pilot and main; check the wiring diagram and make sure your pilot wires go to the PP and PP/TH terminals; make sure the terminals are clean and the connection is good; you are dealing with .320 volts DC, any bad connection drops the voltage below the required minimum.
Posted on Jun 28, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Sep 23, 2014 | Water Heaters
Jun 06, 2012 | Hayward Pool Products Hayward H250 250k...
you for posting your question here on Fixya.com.
Make sure you did not reverse the red and white lead wires from the thermocouple as doing so will not hold the solenoid for the pilot open. If the wires are connected properly start next with the pilot head. You want to be sure the pilot flame is not partially blocked or that the gas mix is poor which you can tell by whether the flame is a nice tall, bright blue color or not.
If that checks out you need to check gas pressures at the inlet to the valve and to the pilot and check the gas valve itself for a bad solenoid.
this answer does not fix your problem, please comment with additional details
prior to rating the answer. You may also contact me thru our website at www.arrowpools.net. Positive feedback is
appreciated once your problem is solved!
Aug 20, 2011 | Hayward H-series Electronic Gas Pool...
May 31, 2011 | Hayward 250kbtu Ng Pool Heater - Inground
Jun 09, 2010 | Hayward 250kbtu Ng Pool Heater - Inground
May 31, 2010 | Hayward 250kbtu Ng Pool Heater - Inground
Jul 01, 2009 | Hayward H Series Pool & Spa Heater 400k...
May 08, 2009 | Hayward H Series Millivolt 250,000 Btu...
685 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: