Question about Coleman Mach 15 Air Conditioner
Is your Air Conditioner run with a wall mounted thermostat or the ceiling pack controls? If it is the ceiling pack controls, then your selector switch has gone bad and needs to be replaced. This is located in the ceiling pack itself and is relatively easy to do. You can easily test it with an Ohmmeter, going through these steps:
To check the selector switch, remove wires from the terminals
and rotate the switch to the proper position and read
continuity as follows:
Terminals Switch Position
L-1-3 Lo Heat
L-1 Lo Fan
L-2 Hi Fan
L-1-4 Lo Cool
L-2-4 Hi Cool
* If you do not wish to remove the wires from each terminal,
disconnect the 9 pin plug from the a/c unit.
Hope this helps,
Posted on Jun 29, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Apr 20, 2017 | Coleman Heating & Cooling
Jul 12, 2015 | Coleman Dometic Duotherm Rv Air...
Aug 18, 2011 | Coleman Mach III Air Conditioner
Dec 16, 2017 | Coleman Mach 15 Air Conditioner
May 25, 2017 | Coleman Mach 15 Air Conditioner
Jul 26, 2010 | Coleman Mach III Air Conditioner
Jun 26, 2009 | Coleman Mach 15 Air Conditioner
Jun 11, 2008 | Heating & Cooling
Jul 15, 2013 | Coleman Mach 15 Air Conditioner
192 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: