Question about Intermatic T104M 208-277Volt 40-amp Timer Switch-Double Pole / Single Throw
I installed a T104 on my water heater, it ran perfectly for twelve hours but when it reached the shut off time of 8 am, it shut the appliance off and the timer clock stopped too. It seems to be wired according to instructions.
The power incoming to the timer (known as LINE) must be on terminals 1 and 3 as this is where the clock gets its power from. The power leaving the timer going out to whatever you want to control (known as LOAD) should be on terminals 2 and 4. This way the timer motor has power all the time.
When the timer is on terminal 1 connects to terminal 2 and terminal 3 connects to terminal 4.
Posted on Jul 09, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 11, 2015 | Hardware & Accessories
Aug 17, 2014 | Refrigerators
May 20, 2014 | RTO Intermatic Inc Ej351c Timer Night...
Sep 03, 2011 | Intermatic T104M 208-277Volt 40-amp Timer...
Feb 22, 2011 | Intermatic T104-20 Indoor Hot Water Timer
Feb 18, 2011 | Electric Intermatic Wh 21 Water Heater...
Feb 02, 2011 | Comfort Zone CZ9009 Oil Filled Electric...
Dec 14, 2010 | Rheem 2.5 Gallon Electric 120V Water...
May 10, 2010 | Intermatic T101R3 110 volt time clock in a...
Mar 17, 2010 | Intermatic T101R3 110 volt time clock in a...
252 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: