Question about Honeywell Programmable Thermostat Heater
When i went to set temp, as soon as i touch controll (temp controll) button AC finally kicked on. why
It could be the thermostat is loose on the subbase or if you went from OFF to COOL and the stat is a digital stat It will not come on for five min. This is a delay set by the manufacture to protect the compressor. during normal operation you will not notice because thier will be more than 5 min from the time it shuts of till it need to come back on but if the system switch is set to off and you switch to cool or unit just shut off it will always delay 5min. usualy there will be some insdiction on the screen that it is in delay like a flashing COOL or SNOW FLAKE or the word WAIT. the unit will not be running until the flashing words go solid
Posted on Sep 12, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 27, 2013 | Maytag M6X06F2A Air Conditioner
Oct 28, 2012 | Honeywell Programmable Thermostat Heater
Jul 21, 2011 | Hunter Heating & Cooling
May 02, 2010 | Sharp AF-S120FX Comfort Touch Air...
Sep 13, 2009 | Honeywell CT87B ROUND HEATING&COOLING...
Jul 27, 2008 | DeLonghi CF210 Portable Air Conditioner
Jun 29, 2016 | Honeywell Programmable Thermostat Heater
Apr 27, 2016 | Honeywell Programmable Thermostat Heater
535 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: