Question about Goodman Heating & Cooling
You have a restriction in the system. Probably in the TXV or orifice in the A/H.
The burn out sent trash/fragments through the system. I would open the sytem and blow nitrogen through, then pull a deep vacuum.
You may need to install a low side filter/drier. When you open the system change out the high side drier again for sure.
Posted on Jun 26, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
May 31, 2015 | Frost Refrigerators
Oct 23, 2013 | Samsung RS2630WW Side by Side Refrigerator
May 05, 2013 | Harley Davidson FLSTF Fat boy Motorcycles
May 06, 2012 | 2002 Honda VT 600 C Shadow
Nov 06, 2011 | 1996 Dodge Intrepid
May 31, 2011 | Weather King 10AJA6001AH Air Conditioner
Oct 25, 2009 | Dishwashers
Sep 24, 2009 | 1980 Cadillac Deville
May 09, 2009 | Heating & Cooling
582 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: