Question about Carrier Heating & Cooling
Ac making buzzing/humming noise when thermostat is turned to the cooling temperature. Fan is not spinning on it's own but I can take a stick to turn it to start it. Capacitor and motor replaced last year. Which direction should it be turning? It will stick start in both directions. Clockwise will blow a lot of air out of the top, but it seems a bit cooler than usual (it's night time maybe?). Counter clockwise will not really blow out the top any air. The motor housing is warmer than it should be this late at night. How do I know which way it should be turning? I don't think the ac in the house either direction is blowing air that is very cool and the thermostat is maintaining, not lowering like it should. I'm hoping if I can keep it spinning in the right direction it will cool the house down a bit for the night until I can fix it tomorrow. (cap. /maybe motor) My wife has MS and can't get hot. Anyone up this late? HELP!
1. Which direction should the fan blades be spinning?
2. One direction blows a lot of air out top like usual but not warm air (it's evening?) the other direction spins doesn't reallly blow any air out the top of unit.
3. Does this sound like the capacitor and how can I tell if my compressor is shot?
The condensor fan should be sucking air from the top and blowing it through the coils, probably a counter clockwise direction. The buzzing/humming sound is confusing to me. A humming sound sounds like a motor that can not turn over to start. A starting capacity would be needed. Just because you changed it out last year does not mean it is good. A buzzing sound sounds like a contactor problem. Contactors buzz and after a while, they will fail. In any case, you can "stick start" the condensor fan PROVIDED you are sure the ac compressor is working (this is for a short and temporary use). Also, you may have a high load duty capacitor that assists in the unit running. This will affect your condensor fan operation if it is not good. Unless you know all the components and operations of ac electrical, I would highly recommend calling out a professional.
Posted on Jun 26, 2009
I am sorry but I have to disagree with what the other guy said.
First, all condensing units suck in through the coils and blow out the top. (it's probably the capacitor why the fan motor wont run.)
Second, you mentioned that it was not warm air like you expected-again the capacitor because on these units the capacitor is a dual job that connects to the fan and the compressor. If it's bad the compressor will just sit there and its casing will get hot.
(it is a bit unusual for both sides of a capacitor to go out so make sure and check for loose wires-in particular the black wire in this case.)
The buzzing sound could be the motor trying to work with a bad capacitor, or it could be the contactor buzzing-no big deal either way, once you fix it that will go away.
Posted on Jan 30, 2015
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 20, 2016 | Heating & Cooling
Dec 01, 2014 | Goodman Heating & Cooling
May 26, 2014 | Empire DV-215 Direct Vent Natural Gas...
Nov 02, 2012 | 2006 Chevrolet Cobalt
Aug 08, 2012 | Ruud Matching Split Air Conditioner
Aug 02, 2012 | Chevrolet Tahoe Cars & Trucks
Aug 02, 2012 | Chevrolet 2001 CHEVROLET TAHOE Chassis...
Sep 10, 2017 | Heating & Cooling
Dec 24, 2010 | Dacor ECS130 Epicure Electric Single Oven
Nov 10, 2010 | LG Heat cool Window Air Conditioner
Jul 02, 2018 | Carrier Heating & Cooling
4,724 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: