Question about Goodman CLQ36AR49 Air Conditioner
Better off taking good money and put into something with a warranty. its probably a 4 hour job to recover solder in new valve change drier pull vacuum recharge If your system is freezing up it may not be the valve could be a check valve. low freon dirty unit all would cause the unit to freeze up is the company competent in working on heat pumps don't get some body that can work on you want in FIXED . from what you said in your 2nd post i am not convinced its the valve. Tom p.s i am in the mid west prices are not too far out of line.
Posted on Jun 25, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 27, 2017 | Goodman Heating & Cooling
May 03, 2014 | Goodman Heating & Cooling
Feb 15, 2013 | Goodman Manufacturing Goodman GSC130181...
Mar 19, 2010 | Goodman CKL42AR42 Air Conditioner
Jun 23, 2009 | Goodman CLQ36AR49 Air Conditioner
May 11, 2009 | Dell Computers & Internet
Nov 13, 2008 | Mitsubishi WD-52525 52" Rear Projection...
Nov 10, 2008 | Amana PTH123B25AJ Heat Pump Air...
First turn the main power off to the unit at the breaker, wait about five min. and switch the breaker back on, then see if this solves the problem. In the instalation manual that came with the unit on the last page you will see a code of the red blinking light, this will tell you the most likely problem if not solved by switching the breaker on again.............Hope this helps
Oct 14, 2007 | Hitachi RAS-09UH Air Conditioner
400 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: