Question about Heating & Cooling
Your system sounds like it is iced. Two usual causes are 1. low on refrigerant (Freon is Dupont's brand name for refrigerant) 2. and/or poor air flow across evap. coil in home. Now when the unit ices air can not get thru the iced evap. coil so it seems like the indoor blower is not blowing hard. Maybe the indoor blower is cause of problem as when they stop or run slow the system will ice, too.
It would be best to have a qualified technician test your system to find cause. You should turn off system until a technician tests it.
P. S. A clogged air filter will cause icing, also!
Posted on Jun 25, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 06, 2012 | 1999 Ford Explorer
Feb 24, 2011 | Heating & Cooling
Jan 24, 2011 | Heating & Cooling
Sep 17, 2010 | Traulsen 24.2 cu. ft. / 685 liter...
Aug 25, 2010 | Honeywell Heating & Cooling
Aug 15, 2010 | DeLonghi Heating & Cooling
Mar 18, 2010 | Coleman (100076) Compact Refrigerator
Jun 09, 2009 | Goodman GMS90703BXA Heater
Jun 25, 2008 | Heating & Cooling
Jun 11, 2008 | Ruud UBHC Air Conditioner
76 people viewed this question
Usually answered in minutes!