Question about Raypak Pool & Spa
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Make sure that gas control knob is set to ON (counterclockwise).
Make sure that ON/OFF switch is ON.
Check that temperature setting is high enough to call for heat.
Make sure pool pump is running and water is flowing to unit.
If not above there is a diagnostic procedure on page 33 of manual at:
Posted on May 30, 2009
What you probably need, you may be able to install yourself and save some$$$. It's call a thermocouple. It's a long thin tube that has a probe bulb at one end and snakes it's way back to the gas regulator.14 years is plenty of service to get from one of these.Don't laugh, but often times you can find a good one on anold gas heater in the metal pile of your local dump. It's worth a peek. If not get one of your heat and cool contractor friends drunk, then ask him to pick one up at the gas company. Town laws vary greatly from town to town. Here in Provincetown we can hardly change a light bulb without a permit...lol. Good luck, I have faith in you. Thanks Dana.
Posted on Aug 21, 2009
press the mode button until the display reads "off". Remove the four screws holding the control cover on. Swing panel down so that the back of the board is visible. Press the mode button until "RESfl" appear. Press and hold both "up" and "down" buttons for 5-7 seconds until three dashes appear (---). This resets the fault history and clears any stored faults.
Posted on Sep 16, 2009
In models older than 07-07 it typically indicates a loss of the pilot light.
In models newer than 07-07 it is probably the air switch not being activated, or it has just failed. Check air switch tubing for secure connections.
Posted on Oct 27, 2010
Tips for a great answer:
Mar 30, 2013 | Raypak Pool & Spa
Oct 05, 2012 | Raypak Pool & Spa
Oct 02, 2012 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
May 24, 2012 | Raypak Pool & Spa
Jan 02, 2012 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Jul 14, 2011 | Raypak 130,000 BTU Propane Gas Pool...
Feb 22, 2009 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
26 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: