Question about Kichler Hardware & Accessories
I need to add a second run to an existing transformer and not sure how to wire the 2nd connection. Any help would be greatly appreciated, I cannot seem to locate a manual, thank you!
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You need to connect one wire from each cable to one of the com terminals. The other wire from each cable has to connect to a tap terminal. The tap terminal you use will depend how many lights and the length of the cable. For short cable runs like 25' use tap 1 50' tap 2 100' tap 3 more than 100' tap 4. you may need to connect all three cables to the same tap terminal. If you turn it on and one string of lights is dimmer than the others move the tap connection from that wire to a higher number. The tap terminals send out a little higher voltage the higher the tap number. The obect is to get the same light output of each light compensating for the voltage drop of the cable. This is a lot of info so I hope this answers your question. If you need more help let me know.
Posted on Dec 04, 2008
Tips for a great answer:
Jul 09, 2017 | Kichler Hardware & Accessories
Feb 21, 2017 | Heating & Cooling
Feb 09, 2013 | KICHLER TRANSFORMERS - PROFESSIONAL SERIES...
Jan 06, 2013 | KICHLER TRANSFORMERS - PROFESSIONAL SERIES...
Jun 28, 2011 | KICHLER TRANSFORMERS - PROFESSIONAL SERIES...
Jun 07, 2011 | Kichler TRANSFORMERS - PROFESSIONAL SERIES...
Nov 02, 2008 | Kichler TRANSFORMERS - PROFESSIONAL SERIES...
47 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: