Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: oil trap for 2 ton split unit
Pipe size is okay, not that I know any better than the manufacturer, but I would recommend at least two and possibly even three oil traps in the vapor line on the way back up.
Posted on Jun 15, 2008
Draim pans do get dirty and partialy block drain pan. If possible take a shop vac and gently **** out the drain line. This will pull the restriction out of the line and help clean drain pan. Rusty
Posted on Jun 07, 2009
The factor that you have not included here is the distance from the power panel to the unit...if it is too far then you need to up gauge the wire to compensate for that... that could be why the electrician wanted to go to the 720 ga. wire.
Posted on Apr 16, 2010
the water comes from the coil, start there make sure there is no obstruction coming out to your condensate line and make sure its properly pitched.
Posted on May 22, 2010
Tips for a great answer:
Aug 05, 2015 | AMVENT 18000 Btu 1.5 Ton Ductless Mini...
Jun 25, 2015 | Mitsubishi Heating & Cooling
Aug 26, 2014 | Heating & Cooling
Mar 10, 2012 | Heating & Cooling
May 16, 2011 | Heating & Cooling
Jan 04, 2011 | Goodman Heating & Cooling
Apr 21, 2010 | Dometic Rooftop RV Air Conditioner
May 01, 2009 | Carrier 36KCARMS Air Conditioner
73 people viewed this question
Usually answered in minutes!