Question about Goodman CLQ36AR49 Air Conditioner
Posted by Anonymous on
You have to have 240 volts for power. 24 volts to operate cool and heat. thermostat feeds color code white to heat yellow to cool green to fan. think of the thermostat as a light switch. transformer in system feeds common to different controls & usually red to thermostat which is then switched to what it is set for.
Posted on Aug 09, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Hi, and yes you have a short in a componant such as a blower motor has quit or shorted out, it could be a number of things. If these units are fairly new, the furnace will have a led light on it that will tell you if you have a control voltage problem, but in this case it trips the 15 amp main. This happens quite a lot. You will need to get to this heater and start looking for anything out of the unusual, burned electrical smell from the windings on the blower motor. You can unplug the blower leads at the circuit board and have someone up top reset the breaker to see if it holds. If so, its the motor that's shot. I know they are hard to work on under the house but you have no choice. You will have to do a process of elimination. It really should be easy to find as it is a dead short on a high voltage part, blower motor, circuit board. Just have a good strong light and have a 5/16 and 1/4 " nut drivers with you. Take a screw driver of each with you also, and have someone up top to work with you. It will save you a lot of time. Keep me posted, please.
Posted on Jun 11, 2010
Tips for a great answer:
Jul 09, 2017 | Coleman Heating & Cooling
Feb 23, 2017 | Heating & Cooling
Apr 17, 2014 | Coleman Heating & Cooling
Jun 12, 2013 | Coleman Haier 3.5 Ton 13 SEER Heat Pump...
Sep 13, 2010 | Carrier BCA101R Air Conditioner
Apr 08, 2010 | Sanyo Split System Air Conditioner
Dec 08, 2009 | Heating & Cooling
Apr 19, 2009 | Goodman CKL49AR49 Air Conditioner
Mar 07, 2009 | Soleus KFR12GWD 12,000 BTU Heat & Cool...
57 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: