Question about Coleman Mach 15 Air Conditioner
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
R = HOT 12V
W= WHT- GND
Y = YELLOW / POSSIBLE THERMOSTAT
G= GRND FOR THERMOSTAT
f = FAN
aSSUMING THIS IS A TWLVE VOLT SYTEM- The two f's Would be fan control intake and exhaust - fan direction
White is always ground and so is green.. green is more of a static ground where white is a load grnd.
Red is always hot. in low voltage
I hope this helped. No instructions in kit?
Posted on May 18, 2009
Soounds as though the motor is getting hot and kicking out on overloads.. best have it checked . But my money is on your going to need a new motor..
Posted on Jul 18, 2011
Tips for a great answer:
May 31, 2017 | Coleman Heating & Cooling
Jul 12, 2015 | Coleman Dometic Duotherm Rv Air...
Apr 19, 2014 | Coleman Heating & Cooling
Apr 14, 2014 | Coleman Home Electric Furnace Eb15b/Eb15d
Jun 10, 2013 | Heating & Cooling
Jun 05, 2013 | Coleman Home Electric Furnace Eb15b/Eb15d
Jul 18, 2011 | Coleman Heating & Cooling
Oct 15, 2008 | Heating & Cooling
Jul 21, 2008 | Coleman Heating & Cooling
May 04, 2008 | Heating & Cooling
Jun 03, 2017 | Coleman Mach 15 Air Conditioner
Jul 15, 2013 | Coleman Mach 15 Air Conditioner
56 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: