Question about Pentair Minimax NT Heater
My heater wants to start but doesn't. Fan turns on when thermostat light comes on. I hear flame for one split second then dies. Fan continues to run. Gives me error code 4- fan failure, even though fan is the only thing working
Sounds like a flame sensor problem. The board is not getting the proper signal from the flame sensor so it thinks the burner did not light and shuts the gas supply off. It keeps the blower operating to ensure that no gas is accumulated in the burner area. I suggest you contact a local mechanical contractor to service your heater.
Posted on Jun 26, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 02, 2015 | Heating & Cooling
Apr 14, 2013 | Heating & Cooling
Ok so here is a sequence of the heater lighting and the solution for your problem...
1. Thermostat calls for heat. 2. Draft inducer motor starts. 3. Pressure switch attached by a small plastic or rubber tube senses the negative pressure produced by the draft inducer and closes. 4. Draft inducer runs for 30 seconds to a minute before you hear a gas hissing sound. The ignitor did not glow, the flame sensor (a small metal probe about 1/8" in diameter, with a white porcelain base) does not sense the flame, so after 8 to 10 seconds the hissing sounds stops with no ignition of gas to heat your home. Your furnace shuts down and goes into a lock out condition until you turn your power switch back off and on again. Then the sequence starts all over again with no ignition of the gas. Solution:You probably need to purchase and install a new ignitor. I would suggest that you inspect your ignitor closely for cracks.Make sure you do not touch the ignitor with your bare hands. If you do not visually see a crack, then you could have a furnace control board problem or a limit, rollout switch problem. Please see "limits, rollout switches & furnace control boards" further down on this page. The furnace's control board might not be supplying the voltage to the ignitor. If your furnace lights and the gas stays on for 8 to 10 seconds, then shuts right back off, then you need to clean your flame sensor with light sand paper or steel wool. You might need a new flame sensor, but most of the time they can be cleaned an will work well after cleaning. Please see the pictures below to help you identify a flame sensor.
Thanks and I hope this helps. Feedback apprec.
Jan 28, 2011 | Honeywell Electronic Programmable...
Dec 17, 2010 | Coleman Heating & Cooling
Nov 23, 2010 | Goodman GMS80453ANA Open Flame Mid-Size...
Nov 19, 2009 | Goodman GMS90703BXA Heater
Jan 19, 2009 | Vanguard International Vanguard BY Rheem...
539 people viewed this question
Usually answered in minutes!