Question about Electrical Supplies
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Generac Guardian 15kW Generator
That sounds just about right, if the relay contacts get welded together it sometimes takes out the driver on the printed circuit board. As you found out, 12vdc from 23 to 194 makes the transfer switch move to the Generator position, relay not energized makes the ATS move to the Normal position.
You can make a nice test function by installing a 10 amp contact switch in series with either the N1 or N2 terminals. When the switch is open the generator thinks the Normal power has failed.
Posted on Jan 26, 2009
1. Does the generator stay running when you start it the first time?
2. What color is the housing on this generator? Try to get the model number and serial number.
If the genset is shutting down on the first try, then your probably not creating voltage. However, if this is an older unit then the genset may stay running although no voltage is created. Place a volt meter on the genset to check for output voltage.
Posted on May 10, 2009
I install and work on these everyday. If you hooked up the transfer switch you probable have a control wire wrong. check the utility power sense wire. That lets it no when to start in auto. it could be a relay or fuses. or a control board.
Posted on Jul 09, 2009
Tips for a great answer:
Jul 19, 2013 | Kohler Electrical Supplies
Sep 29, 2012 | Kohler 100-Amp Automatic Transfer Switch ...
Jun 27, 2011 | Kohler 12 kW Emergency Power System -...
Mar 09, 2011 | Generac Guardian RTSE200A3 200 Amp...
Sep 16, 2010 | Kohler 100-Amp Automatic Transfer Switch -...
Mar 08, 2010 | Kohler 100-Amp Automatic Transfer Switch -...
Dec 31, 2009 | Kitchen Appliances - Others
Sep 02, 2009 | APC Automatic Transfer Switch (AP7701)...
Aug 08, 2009 | Kohler 12 kW Emergency Power System -...
243 people viewed this question
Usually answered in minutes!