Question about Electrical Supplies
Posted by Anonymous on
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
the instructions says the voltage regulator is automatic/digital. when you check the voltage is there any load on the generator? if applying load to the generator doesn't help, you can manually change the motor speed where the governor connects to the carborator, but it may change the frequency, but the regulator may fix it
Posted on Apr 13, 2009
Before you adjust anything, suggest you verify gas line for proper pressure and importantly volume. Pressure for gas should be 5 to 7 inches and propane 11 to 14 inches W.C. Also make sure the line to the generator is sized properly and the gas meter is a high volume unit (if NG). 90% we find the problem with generator sunder load that otherwise are fine are fuel related. Good luck.
Posted on Sep 19, 2012
Tips for a great answer:
Dec 19, 2016 | Generac Electrical Supplies
Feb 16, 2015 | Generac Electrical Supplies
Jan 07, 2015 | Generac Electrical Supplies
Nov 03, 2012 | Generac 5606 XP Series XP8000E 12,000 Watt...
Feb 16, 2011 | Generac 5606 XP Series XP8000E 12,000 Watt...
Jan 04, 2011 | Generac 5606 XP Series XP8000E 12,000 Watt...
Dec 23, 2010 | Generac 5606 XP Series XP8000E 12,000 Watt...
Feb 07, 2010 | Generac 5622 GP Series GP5000 6,250 Watt...
Apr 12, 2009 | Guardian Electrical Supplies
33 people viewed this question
Usually answered in minutes!