Question about Bryant Heating & Cooling
4 ton seer 563CNO48-D compressor 208/230. The outside unit has stopped running, the outside unit hums loud gets hot but the fan does not turn nor does it cool the house. The fan in the house for the unit blows
Posted by Anonymous on
Can be a bad fan motor, defective capacitor or contactor issue. capacitor is cheapest fix if bad.
Posted on Aug 05, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: outside makes loud noise
I would take a very close look at every solder joint there is between the inside unit and the outside. If you observe oil at any point it indicates a leak at that point. That is an expensive price for what you say was done. Check your invoice for the amount of refrigerant they or he added to the system. Compare it with the amount stated on the outside unit nameplate. Check for frost on the suction (big line) by the outside unit. If there is frost your coil is frozen up. If this is the case turn the fan on and the cooling off. Allow it to run in this manor for about an hour to defrost the A coil. Then return to the cooling mode.
Posted on Jun 16, 2008
open the service panel to check for control voltage of 24volts when tstat calling, The contactor should be pulled in, if contactor is down,and contacts appear to be clean, and the unit is still not running, it is a bad compressor. to test this unplug the black wire from the compressoror at contactor,w/ power off! Turn on power if fan works normally it's a bad compressor. However if you see a swollen split cap(5 wires to a soup can looking w/ the terminal C,F,and Comp), switch it first and start at square one.
You also need to consider the high pressure switch if its cycling on off on off.
Posted on Mar 12, 2009
first look for red button neer the copper line set if has one push it second inspect thermostat wires for weed eater damage check disconnect for fuses check breaker at main panel pull disconect and remove cover check stat wire connections look at the capacitor if swelled up on top bad if all look ok put disconect in using insulated object manually push in contactor if unit comes on check for 24 volt ac on yellow stat wire to common if none stat wire could be loose at indoor unit or stat bad hope this helps you
Posted on Jun 06, 2009
are you speaking of the outside fan or inside? compressor should be a little warm but not boiling hot. the unit could be low on freon. if low it will run a while but the compressor will overheat and shut off leaving the fan running by itself ouside. if nothing outside is running check power. if you have power check the contacted outside to make sure it's pulled in. contacters are bad about going out on goodman untis. Also ants can get under contacts.
Posted on Jun 18, 2009
Souns like the compressor is running but the cooing fan is not. First you should see if the fan is blocked . Then see If the fan motor is getting power. If the motor is getting power it could be that the motor is bad. If the motor needs a capacitor to start that could also be the problem. Look for a cylinder shaped protrusion on the side of the motor. If these all check out then whatever tells the fan motor to come on is not working. Sorry but I cant help with that. Good luck!!
Posted on Jul 05, 2009
Tips for a great answer:
Apr 19, 2016 | Heating & Cooling
Jun 23, 2014 | Bryant 2 Ton 17 Seer Air Conditioning...
Jun 22, 2014 | Carrier 3 Ton Infinity Puron A/c outside...
May 11, 2013 | Ruud 3 Ton Split System Heat Pump
Sep 27, 2012 | Goodman Manufacturing Goodman GSC130301...
Feb 01, 2011 | Samsung AS18A6RB Air Conditioner
Sep 22, 2009 | Heating & Cooling
Jul 31, 2009 | Haier HC48C1VAR Central Air Conditioner
Jul 25, 2009 | Heating & Cooling
May 28, 2008 | Ruud Matching Split Air Conditioner
66 people viewed this question
Usually answered in minutes!