Question about Traulsen Commercial 2 Door Cooler / Refrigerator
Ok, next question, when he replaced the compressors, did he modify the evap sections with TX Valves and remove the cap tubes? Per Traulsen specs, all remote units are factory set with TX valves while local units are equipped with cap tubes. If this modification was not done, it may be your cause of excessive electical consumption. Then again, re-reading your recent post, the compressors were changed to 3/4 hp? From Traulsen specs your unit came with a 1/6 fridge compressor and a 1/3 freezer compressor, is that correct? Electrical consumption on these are URS48DT 11.2 Amps 1/6 HP & 1/3 HP (1288 watts) at full load, while a 3/4 compressor is 14.9 amps 3/4 HP (1713.5 Watts) at full load X2 = 3527 Watts, or about 3 times original. I may be off target, but from what I can assume, I am beginning to think your compressors are over sized, drastrically and that the evap units may not have been modified to TX Valve. Let me know if this helps or if there is any additional information you can provide. Current compressor model numbers, previous compressor model numbers, complete unit model/serial number would all be a help in determining your exact specifications.
Posted on Jun 23, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
May 04, 2018 | Traulsen Freezers
Aug 16, 2014 | Refrigerators
Aug 15, 2014 | Televison & Video
Sep 25, 2010 | GE Refrigerators
Sep 04, 2010 | Office Equipment & Supplies
Jun 05, 2010 | Traulsen UR48DT-6 Refrigerator/Freezer -...
Oct 12, 2009 | Refrigerators
Jul 04, 2009 | Traulsen Refrigeration 48'' Wide x 24''...
Jul 16, 2008 | Traulsen Refrigerators
Jan 20, 2008 | Traulsen 7 cu. ft. / 198 liter Commercial...
371 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: