Question about Balboa Instruments Pool & Spa
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: No Heat from Spa
Heater contactors "buzzing": Do you mean normal buzzing or extra loud buzzing? Loud buzzing or chattering can be caused by low voltage to a contactor. If normal sounds, then probably the relays on the contactors is working, but the contacts may be stuck, or burned enough so as not to make contact. First, get a voltmeter and check for 240 volts AC at the heater contactor terminals. If the voltage is low, most likely you need to check the contactors further. Check for dirty contacts, clean if needed. If the contacts are not moving when energized, then you will probably need to replace one or both of the contactors.
Posted on Jan 18, 2009
hello, It sounds like you may not be getting circulation thru the heater. Make sure the valves are open to allow water to pass thru the heating system. Some systems use a bypass on the heater so there is not a lot of wear on the coil system in the heater. If it is not circulating it will get too hot and the safety shut down will occure. If you are getting water circulating thru the heater, then the thermocouple or auto start igniter system is not working correctly. It is trying to start and can't then recycles. If the burners are igniting on the startup and then shutting back down you may have a bad control unit or thermal sensor unit. Since the unit is gas have a professional service it for you. Good Luck, RAC
Posted on Apr 20, 2009
SOURCE: spa wont heat
Check the pump make sure that it is getting power. If there is power to the pump and nothing is working then pump is bad. Also this could be your computer board is bad, a inline fuse. or the Jandy is bad
Posted on May 20, 2009
SOURCE: layz spa pump
same problem I had so I seperated the globe by taking out the 5 screws around the middle then removed the nut from the hole the filter sits on its a strange fitting and must have a special key but I improvised by tapping it anticlockwise using a screwdriver and rubber mallet, once open identify the heater unit (it has a single wire going into it and is fastened to a length of metal pipe) and remove it by loosening the clamps at either side and pull the heater free, once free dismantle the plastic casing on the top of the heater inside you will see the live, neutral and earth wires, you can see the live (brown) wire goes to the water flow switch then the temp switch then the heater all I did was bypass the water flow switch by disconnecting the short wire from it going to the heat sensor and replacing it with the brown wire coming from the mains and it works fine now
Posted on Aug 02, 2009
SOURCE: I want to heat the
When your system is put into Spa mode the system draws water from the spa only to the heater to keep the spa at temp, this is why the overflow doesn't work and why you can not heat the pool in spa mode. If you could heat the pool this way it would take a very long time, since the spa is smaller then the pool. You can heat the pool and spa at the same time in pool mode. Water is pulled from the pool, heated and goes back into the pool and spa.
Posted on Apr 02, 2010
Tips for a great answer:
Aug 09, 2016 | Pool & Spa
Sep 08, 2015 | Balboa Instruments Pool & Spa
Feb 23, 2015 | Pool & Spa
Nov 18, 2013 | RTO Balboa, Heater w/Pressure Switch
Jun 20, 2017 | Pool & Spa
May 19, 2011 | Balboa Instruments BALBOA 30 kW HEATER W...
Feb 14, 2011 | Balboa Instruments BALBOA 30kW HEATER ASSY...
Sep 13, 2009 | Balboa Instruments Duplex Digital Panel 2...
114 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: