Question about Bosch AquaStar 2400ES-NG
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
if you have incorrect gas line size when it kicks on the lack of gas pressure to the unit will cause a wistling. make sure you have enough gas to the unit
Posted on Jul 29, 2009
The 250 MUST have the condensate line connected. EC comes from gas supply problems and CO2 levels not being adjusted. LP units require 3/4" smooth gas pipe or 1" corrugated pipe minimum size. The LP regulator needs to be turned up to about 13 inches of water column and with all the gas appliances on, measure no less than 11 inches of water column. The CO2 levels must be measured by a qualified gas technician with a calibrated (with in 6 months) CO2 analyzer.
Posted on Apr 11, 2010
Tips for a great answer:
Mar 27, 2014 | Bosch AquaStar Indoor Natural Gas Tankless...
Apr 16, 2011 | Bosch AquaStar Indoor Natural Gas Tankless...
Sep 04, 2010 | Bosch AquaStar Indoor Natural Gas Tankless...
Jan 06, 2010 | Bosch AquaStar 2400ES-NG
Jul 13, 2009 | Bosch 2700ES Natural Gas AquaStar ...
Jun 09, 2009 | Bosch AquaStar Propane Tankless Water...
Mar 04, 2009 | Bosch 1600H-NG Natural Gas AquaStar...
54 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: