Question about Goodman CKL30AR30 Air Conditioner
Control wires come from the thermostat to power the contactor coil. At the thermostat the red wire must power (switch) the yellow wire to make the contactor pull in to run the outside unit, Check power with a ac volt meter between the red wire and the yellow wire, with the heat/cool switch turned to off. If you do not have 24 volts ac, your wire may have an open from the thermostat to the outside unit, your transformer may be bad and not supplying power, or your contactor coil may be open
Posted on Jun 23, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Oct 04, 2014 | Carrier Comfort 3.0 Ton 13 Seer Ac Only...
May 08, 2014 | Goodman Manufacturing Goodman GSC130421...
Dec 04, 2013 | Ruud UAKA037 Air Conditioner
Oct 30, 2013 | Hunter Fan Company 42999B - Heat/Cool...
Aug 26, 2013 | Honeywell PRO 4000 5-2 Day Programmable...
Jul 25, 2017 | Heating & Cooling
Sep 09, 2011 | Honeywell Heating & Cooling
Aug 03, 2011 | Heating & Cooling
Jul 30, 2009 | Heating & Cooling
Jun 07, 2009 | Goodman CKL24AR24 Air Conditioner
Aug 06, 2011 | Goodman CKL30AR30 Air Conditioner
913 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: