Question about Cozy (W352E) Heater
This heater has worked well for the past 20 years, the pilot will light , but when I turn up the thermostat it clicks and shuts off the pilot, I replaced the the 750 millivolt generator, but the problem persists, I then replaced the gas valve (model 710-502 robert shaw ) and the problem persists. the piolt lights and stays lit, till I turn up thermostat, and I here a click and the pilot goes out. bypassed thermostat and the same result. any advise would be appreciated.
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
you need to check the generator in series with flame present. remove one wire from gas valve.put 1 of your meter probes under gas valve terminal where you removed one lead from powerpyle generator.put generator on other probe anything over 600 mv and your generators is ok under replace
Posted on Feb 17, 2009
Tips for a great answer:
Apr 27, 2016 | Water Water Heaters
Aug 04, 2015 | Honeywell Water Heaters
Feb 18, 2015 | Williams Wall Heaters: 50,000 BTU/Hr...
Jan 06, 2015 | Heating & Cooling
Jun 01, 2014 | Raypak Pool & Spa
Dec 24, 2013 | Heating & Cooling
Nov 27, 2010 | Heating & Cooling
Nov 12, 2010 | Montgomery Ward (223600UP) Heater
Mar 04, 2010 | Heating & Cooling
Jan 19, 2010 | Heating & Cooling
185 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: