Question about Heating & Cooling
I have never seen one that doesn\'t suck air in through the coil and blow out the top. My guess is that the double shafted motor was installed backwards.
Posted on May 10, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Yes. It should blow out the top. The rotation of the fan does determine the direction of air. Either have the motor replaced and indicate the direction of rotation.
Posted on May 08, 2009
You need to call a reputable service technician. The freezing up usually is associated with a low refrigerant charge or low air flow. Check your return air filter and replace as needed.
Posted on May 30, 2009
The blowing fan is not rotating at the rated speed. Check the fan capacitor and replace.
Check motor also if the capacitor is not at fault.
Posted on May 27, 2010
Tips for a great answer:
Oct 25, 2012 | Coleman Heating & Cooling
Sep 13, 2012 | Coleman Heating & Cooling
Jul 02, 2012 | Coleman Heating & Cooling
May 28, 2010 | Coleman Heating & Cooling
Sep 09, 2009 | Coleman Mach III Air Conditioner
Jul 27, 2009 | Heating & Cooling
Jun 14, 2009 | Coleman Heating & Cooling
Jun 05, 2009 | Heating & Cooling
Oct 18, 2017 | Heating & Cooling
54 people viewed this question
Usually answered in minutes!