Question about Carrier Bryant Condenser Fan Motor HC39GE226
Fan getting very noisy. How difficult is it for me to swap out old with new fan motor? This is a Carrier A/C with OEM part HC39GE226.
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
plz check if there is anything obstructing the fan movement.if not then the motor is the culprit.
It will be better if you leave it for professional
Posted on Jun 07, 2008
use a seperate capicitor for the fan only pick up 1 leg of power from common side of the compressor cap and the other from the contactor or the board in a heat pump situation
Posted on May 11, 2009
With power off, locate fan motor capacitor (generally silver in colour).
Rating on capacitor will be in microfarads at specified voltage ( 5mf @
370 volts). Be careful to discharge before handling and return defective
cap. to source of replacement. They can confirm whether or not truely
defective. Replace and secure. Restore power and check operation.
Purpose of run capacitor is to provide starting torque that you are
presently providing by hand spinning. Hope this helps.
Posted on Aug 05, 2009
there is a run capacitor is probably bad.
you can purchase a replacement one from slakey brothers. However the capacitor will still have a charge after the power and wires are removed. after turning off the breaker use a long bladed screw driver and ground the electrical leads to discharge the capacitor before removing. take it with you to the supply house along with the model and serial number of the condensing unit.
Posted on Apr 15, 2010
Tips for a great answer:
May 19, 2016 | Carrier Heating & Cooling
Mar 15, 2013 | Carrier Heating & Cooling
Sep 18, 2012 | Carrier 38CKC036 Air Conditioner
Jul 19, 2012 | Carrier Heating & Cooling
Sep 07, 2011 | Heating & Cooling
Aug 12, 2011 | Carrier 38CKC036 Air Conditioner
Jan 21, 2010 | Carrier Heating & Cooling
Dec 17, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jul 28, 2008 | Carrier 38CKC036 Air Conditioner
22 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: