Question about Goodman Manufacturing Goodman GSC130421 Air Conditioner 13 SEER Dry Charged 3.5 Ton
Compressor will not run
Posted by Anonymous on
This can be for a variety of reasons. It ranges from something as simple as no supply power (blown fuse, open breaker, faulty contactor, or run capacitor) or it could be more serious as a grounded or open winding in the compressor motor. My suggestion to any novice and or person without proper tools and knowledge; First check the low voltage (24 volt control voltage) by turning on the "Fan on" switch located on the thermostat to on, not "Auto" The blower fan should come on, indicating there's 120 volt and 24 volt available. Fan doesn't come on is an indication that there's no control power. The next step would be to check for power at the transformer and fuse located in the air handler. There should be 240 volts feeding the transformer, and 24 volts coming out. The control voltage is needed to operate the thermostat (which is the switch that sends the 24 volt signal to the compressor contactor to turn the compressor on/off. This 24 volt also powers other relays and switches in the system. knowing that 24 volt is available also tells you that the problem is most likely in the condensing unit (outside, where the compressor is located). At the condensing unit you should check for 240 volt supply power. Upon finding 240 volt supply power the question now becomes whether or not the thermostat is calling for anything (cool or heat if the unit is a heat pump). There should be 24-30 volt available at the small gauge wires feeding the contactor coil. While having the thermostat set at a temperature lower than the current room temperature (in the cooling mode) the thermostat should send a 24 volt signal to close the compressor contactor and turn it on. The non-metallic end of a screwdriver can be used to depress the moveable part of the contactor. After pushing in the contactor, should the compressor start then you may only need a new contactor. It may just hum because of a faulty run capacitor or grounded or shorted internal motor windings (grounded or shorted windings are usually indicated by tripped circuit breaker and/or blown fuse). It's a good idea to have a good multi-meter and knowledge of use before attempting any repairs or diagnosis on your own. I recommend some basic knowledge of electricity before even thinking about attempting any repairs or diagnosis.
Posted on Jan 25, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 25, 2014 | 2008 Dodge Ram Pickup 1500
Jun 04, 2013 | Frigidaire FAX054P7A Wall/Window Air...
Jan 31, 2013 | Cars & Trucks
Jul 04, 2017 | Campbell Hausfeld 26 - Gallon Air...
Aug 15, 2012 | Craftsman 33 gal Air Compressor 6 hp...
Jul 25, 2012 | Makita Mac5200 138a 3 Hp 5 Gal Wheeled Air...
Jul 03, 2012 | Chevrolet Cars & Trucks
Jun 15, 2012 | True GDM-10 Refrigerator
88 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: