Question about Heating & Cooling
Hi Vulcan Bonaire,
Is this a ducted gas heater or a free standing gas heater???
Posted on Jul 03, 2014
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I Also have the same and other problems with my furnace model # GDS80703AXBB. First the LED kept blinking 4 times and I too jumped the primary limit, that didn't kelp. After several attemps I moved the wires going to the circut board and everything starting working again. After a week It stopped working again, so I pulled the plug out of the circut board checked all wires for for a bad connection plugged it back in. Now the LED blinks 6 times again I move the wires. Then the LED blinks 3 times. Then the transformer burns out. I have burned out 2 transformers and I have ordered a new circut board.
Posted on Nov 15, 2008
SOURCE: I have a similar problem
I just went into the Bonaire website and downloaded their FAQ on gas ducted heating from their support link. Their instructions are pretty easy to understand.
Posted on Sep 09, 2009
Here is a link to the manual for your unit heater:
The 4 flashes is a high limit or roll out switch is open. There are 2 or 3 little brown or black button looking switches with a little button on the top and a wire attached to each side. Press the button on each, you may hear a slight "click". If you do, that is the one that was open. Hope this helps.
Posted on Nov 04, 2009
Sounds like you are talking about the indoor fan that circulates air through house. Turn the unit off and make sure the fan rotates freely. Next check the capacitor for the fan. If it looks swollen its probably bad. If it doesn't look swollen then you will need a multimeter to check it with. If that's ok then check the fan relay. Let me know what you find.
Posted on May 30, 2010
Tips for a great answer:
Jul 12, 2016 | Cars & Trucks
Jun 20, 2016 | Heating & Cooling
Mar 10, 2015 | Vulcan Heating & Cooling
May 10, 2014 | Heating & Cooling
May 17, 2011 | Heating & Cooling
479 people viewed this question
Usually answered in minutes!