Question about Goodman Heating & Cooling
If the fan just hums and if you spin the fan and it runs, check out the capacitor, it is bad. Most condensing units have a split capacitor, for the hermedic unit and the fan. If the compressor runs the dual capacitor is bad on the fan side. Your choice buy the dual capacitor, or just buy a single capacitor for the fan part of it. Make sure the voltage rating and microfarad ratings are the same. They will be marked on the old capacitor, as will fan (for fan), and herm for compressor). THATS 220 VOLTAGE YOUR WORKING WITH, BE SURE THE POWER IS OFF!!
Posted on Jun 23, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 21, 2015 | DeLonghi Heating & Cooling
Aug 12, 2014 | Heating & Cooling
Jun 09, 2012 | 2004 Lincoln LS
Apr 16, 2012 | Heating & Cooling
Sep 12, 2011 | Dometic Rooftop RV Air Conditioner
Apr 12, 2011 | Kenmore 75085 Air Conditioner
Feb 28, 2010 | 2001 Ford Windstar
Jun 27, 2009 | Samsung AW0603B Air Conditioner
Jun 16, 2009 | 1995 Saturn Sc
309 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: