Question about Heating & Cooling
My ac compressor starts and stops after every five to ten minutes.
Check the fan is running to cool the condenser, and the condenser is nice and clean
Posted on May 07, 2014
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
eventually,cycling process is doing done if the thermostat sense the configure temperayure set up it will trigger to stop your compressor motor as well as the blower fan,blower fan independenly to you compressor.if your thingking that your compressor is tripping off,check your operating current on one line using clamp ammeter and compare to the rated current that tag on
motor compressor body,if the current flow is higher than the rated current specified on compressor motor,well problem occured it will trip your compressor,because overload protector is becoming your thermostat.but if you got same current result it was cycling process.If tripping off maybe air is present in your system call qualified ac tech, to purge out air in system.
Posted on Mar 16, 2009
Hi, the only thing that could cause this to happen would be the thermostat. This is the main part that controls the roof top unit, getting its signal from the stat to come on and maintain the correct temperature. I would replace it with the same type and this will solve your problem. The only other thing that would cause any unit to cycle like this is if you had bad thermostat wiring touching together some where. I don't think this is the problem with yours though. With the stat off and it still cycles on, this tells me for sure it is the stat. Change it out and you will be good again.
Posted on Mar 26, 2010
i hanve 1.5 ton window air condtioner.compressor of a.c runs for 2 min and he it cuts off after 3 min it again starts
Posted on Jul 27, 2010
Tips for a great answer:
If this isn't the problem the AC compressor relay may also cause this, flip a coin.
Sep 13, 2012 | 1999 Ford Taurus
Nov 06, 2011 | 2002 Saturn VUE
Mar 23, 2011 | Haier Chest Freezer HNCM070E
Feb 17, 2010 | Samsung AW1293L Air Conditioner
Jul 28, 2009 | Ford Ranger Cars & Trucks
Oct 13, 2007 | Whirlpool ED0GTQXMQ Side by Side...
May 20, 2018 | Coleman Heating & Cooling
27 people viewed this question
Usually answered in minutes!