Question about Heating & Cooling
You air conditioning system is designed as an entire unit. All the parts were selected to work together.
The condenser fan motor has been selected to match system voltage, provide enough horsepower and RPM to spin the a fan with "x" number of fan blades with fan blade pitch or angle that will pull enough air across the condenser coil to cool the hot refrigerant gas enough so that by the time it reaches the expansion valve it will be in the ideal temperature range to provide maximum cooling in the evaporator coil.
Changing components with unlike replacements creates strain, inefficient cooling and potentially early failure of parts.
Posted on May 07, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Yes, that can be confusing...hook the tan wire with the white strip onto the same line wire as the one going to the capacitor...usually the L2 wire....so then in reality you have the two tan wires hooked onto the common and the F terminals of the cap...
Posted on Aug 16, 2010
The tan/white wire can be insulated/capped and not used. Use and ohmmeter to take a resistance reading between the tan/white wire and L1 & L2. There will be no resistance between the tan/white wire and one of the others. This will be the common wire. Connect it to one side of the contactor. Connect the tan wire to the fan terminal on the contactor and the other wire to the common terminal on the capacitor (that is if you have a 3 terminal capacitor, if you have a 2 terminal capacitor connect tan to one side and the other wire to the other). Then connect the other side of the contactor to the common terminal on the capacitor (on a 2 terminal capacitor connect the contactor to the side that doesn't have the tan wire on it).
Posted on Aug 16, 2010
SOURCE: NEW CONDENSER FAN MOTOR DRAW
The capacitor may be weak if it has not been changed with the motor, which will cause excessive amp draw. Also may need condensing coil cleaning to reduce static pressure on the fan.
*Some motor ratings do not reflect what is actually needed for proper operation in some cases a higher amp motor is required.
Posted on Aug 27, 2011
Tips for a great answer:
Oct 30, 2015 | Refrigerators
Aug 27, 2011 | Amana Heating & Cooling
Aug 26, 2011 | Goodman CKL60AR60 Air Conditioner
Jun 18, 2011 | Kitchen Ranges
Feb 22, 2011 | Magic Chef MCBR440 Compact Refrigerator
Jun 21, 2010 | Goodman CLQ36AR49 Air Conditioner
Dec 11, 2009 | Video Game Consoles & Games
Aug 14, 2009 | Refrigerators
Aug 02, 2009 | Heating & Cooling
Oct 02, 2008 | Maytag Refrigerators
44 people viewed this question
Usually answered in minutes!