Question about Raypak Rp2100 Pool & Spa Heater Lonox 407k Btu Natural Gas Polymer Header Digital Rp407aenc
I have the exact same problem. My RP2100 was installed in 2002 and the LCD display got worse every year until now, with nothing being displayed. All the research I've done says that there is no way around it - you have to buy a new PC Board: part# 010253F. You can get them on some web sites for about $300 and try installing yourself. I've talked to a qualified RP service person that gave me an installed price over double that, so I think I'm going to try to install on my own.
Check grounds to board also check transformer for voltage look for blown fuses
Posted on May 19, 2016
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Yes its faulty PC board.As no Power Coming from the board.Click this link directly to get PC board.
To confirm the fault in PC board.
Check for exact 24 volts on PC board.
One yellow and One Blue wire.
For checking transformer check
120/240 volt to transformer(time clock circuit breaker wire connections).
Thanks. Keep updated for any more query. You can rate this
solution and show your appreciation.
Posted on Jul 10, 2010
Were the ignitor and the board replaced because of this problem and its still happening? If so, it is probable an incorrect gas supply. If you know the gas supply is adequate, then power is not getting to the ignitor or power is not being distributed from the board. As you stated they are new, it gets alittle more indepth. If there is an incorect gas supply or if the refractory kit is flaking (finding white stuff on the burner tray) then you are probably getting an incorrect burn which will melt through the ignitor wires over and over againm until either venting or gas supply is fixed. If you have a flex line as your gas supply that could be the issue. If the venting is not correct this could also cause this.
Posted on Oct 27, 2010
Tips for a great answer:
Feb 07, 2012 | Computers & Internet
Jun 30, 2011 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Oct 15, 2010 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Jan 02, 2018 | Toshiba 42LX177 42 in. LCD HDTV
Dec 29, 2009 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Nov 10, 2009 | Dynex 32 in. LCD Flat-Panel HDTV
Oct 26, 2009 | Gateway MX3215 Notebook
Sep 08, 2009 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Jun 19, 2009 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
420 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: