Question about Heaters
I've got a Cadet C122 wall heater that quite working. There's 240V to the heater and continuity across the reset switch. No continuity across a round metal device that's at the top of the heater above the coils. Is this normal or is this a shutoff device that can't be reset? If so can it be replaced or do I need to replace the heater? Thanks!
That round metal thing is called a klixon overload. look on the side of it and an amperage range should be there. replace the unit and the element should work unless the element itself is blown. check for continuity across the element with your meter with the wires disconnected.
Posted on Nov 04, 2007
Tips for a great answer:
Oct 18, 2014 | Cadet Manufacturing Heaters
Feb 26, 2011 | Broan-NuTone N-9192NT Wall Heater Heater
Nov 10, 2010 | Cadet Manufacturing C152 Com-Pak Plus...
Jan 25, 2010 | Cadet Manufacturing CADET SL Series Small...
Dec 31, 2009 | Cadet Manufacturing 67507 Heater
Feb 11, 2009 | Cadet Manufacturing 09954 Baseboard Heater
Jan 17, 2009 | Cadet Manufacturing 67507 Heater
Sep 11, 2008 | Heaters
Mar 25, 2008 | Cadet Manufacturing 09950 Baseboard Heater
Oct 23, 2016 | Heaters
902 people viewed this question
Usually answered in minutes!