Question about Goodman GMS90703BXA Heater
There is a sensor that senses if the heater has an adequate VENT like an oxygen sensor on a car, if that has gone bad the heater will think the blower is not blowing and shut everything down to avoid building up gases in the home.Also check the tube that vents to the outside.If it is clogged the same problem will occur.I am no expert but when my heater went out last year I was forced to learn the ins and outs of heaters.HOPE THIS HELPS.
Posted on Nov 03, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 04, 2013 | Cars & Trucks
Aug 03, 2012 | 2002 Dodge Grand Caravan
Sep 06, 2011 | Goodman Heating & Cooling
Jan 24, 2011 | Nissan Pathfinder Cars & Trucks
Jul 11, 2009 | 2001 Oldsmobile Aurora
Jun 16, 2009 | Goodman CLJ36AR42 Air Conditioner
Mar 08, 2009 | Honeywell Power Humidifier: Furnace...
Jul 31, 2008 | 2001 Jeep Grand Cherokee
94 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: