Question about Goodman CLQ36AR49 Air Conditioner
This has happened twice this year and after it happened the first time i checked voltage and lost voltage to fan the fan turns free you can spin it easy. Let system cool down overnight and checked again and fan worked fine didnt need air for a couple weeks. This time it ran for 4 days fine and last night the the fan quit running checked voltage and there was no voltage to fan motor left off overnight and this morning system runs fine. What is wrong with system it is and older rheem system
It sounds like the fan is over amping itself and shutting down on thermal overload check the amp draw during running time and compare it to the sticker on the outside panel it should be running .9 amps, and it will over heat if it runs around 1.2 amps or above
Posted on Jun 21, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 30, 2014 | Heating & Cooling
Aug 28, 2013 | 2002 Dodge Dakota Club Cab
Jul 02, 2011 | Electrolux FRA102BT1 Air Conditioner
May 18, 2010 | Carrier 38CKC036 Air Conditioner
Jul 03, 2009 | Dell Dimension 3000 PC Desktop
Jun 06, 2009 | Goodman CKL42AR42 Air Conditioner
Aug 19, 2008 | Whirlwind FH-778 Air Conditioner
Jul 03, 2008 | Carrier Heating & Cooling
May 17, 2008 | Heating & Cooling
Aug 26, 2007 | Ruud UAKA037 Air Conditioner
228 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: