Question about Hayward 250kbtu Ng Pool Heater - Inground
Place the heater in the heat mode. The blower comes on. In 4-5 seconds the heater will light. It will stay lit for 2-5 minutes and then go out. The problem code will indicate IF or LO and the will go to the ''service mode''.
Sounds like a flame sensor.remove ignitor assembly and clean with fine emory cloth or steel wool.when properly cleaned it should feel smooth for entire length of sensor
Posted on Jun 21, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jun 25, 2014 | Jandy Lite 2 Natural Gas Pilot Light...
Aug 12, 2012 | Hayward H-series Electronic Gas Pool...
Jul 30, 2012 | Hayward H-series Electronic Gas Pool...
Jun 06, 2012 | Hayward Pool Products Hayward H250 250k...
Apr 22, 2012 | Hayward 250kbtu Ng Pool Heater - Inground
Jun 14, 2011 | Hayward H Series Electronic Ignition...
May 31, 2011 | Hayward 250kbtu Ng Pool Heater - Inground
Apr 16, 2012 | Hayward 250kbtu Ng Pool Heater - Inground
May 20, 2011 | Hayward 250kbtu Ng Pool Heater - Inground
1,222 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: