Question about LG LSC183VMA Split System Air Conditioner
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The first thing i'll say is you will need to get it repaired by a technician and i strongly recommend you not to do it by urself.
Remote control units have diagnostic program in the
control, after 3 to 5 minutes of operating if the diagnostic
tools detect abnormal operation, then its shutdown the unit
to protect from damage. Thermistor sensor is one of the
parts that detect the operation of the unit. Out of range
or defective thermistor can shut the operation of the unit.
- If your indoor and outdoor is clean start the unit in cool mode and monitor the outdoor pipes. If your suction pipe is icing or dry then your unit is under charge, but if your suction is cold and sweating then the system is ok and sure that the thermistor sensor is defective.
- Out of range thermistor sensor in both return air and freeze up sensor can cause the tripping “off “ the unit.
Posted on Mar 22, 2008
SOURCE: LG SPLIT SYSTEM AC.
Fixed fault by not only switching off AC unit at power point, had to pull out plug top & lead from wall for one minute. This must allow electronics to reset.
Posted on Feb 01, 2009
Check your remote control using your camera or cellphone camera as your eyes. Point the remote control transmitter to your camera and "on", light should emit in your remote control transmitter (means good remote). Reset the unit by disconnecting the power supply for 10 sec. then "on" again and start the unit. If it wont work you need a qualified tech. to solve the problem.Some of your safety device might be defective.
Posted on Feb 16, 2009
The unit is designed to run the indoor fanmotors continuously when in cooling mode on both indoor units (evaporators). The reason is that this circulates the air and the temperature thermistor or sensor is able to sense return air temperature and in turn start or stop the outdoor unit and compressor as required according to the setpoint temperature. The reason for either unit not reaching setpoint temperature can be a couple of reasons. A) Incorrect design - the unit may be too small for the application. You can calculate this roughly at 650BTU per square meter of room in a relatively warm ambient climate. Or secondly B) The outdoor unit has leaked and is short of refrigerant. You can check this when the outdoor unit is running by feeling the thicker copper tube on the right hand side of the unit. This should be cool to cold. If no temperature difference is felt, it is short of refrigerant. Hope this helps you. Goodbye
Posted on Mar 20, 2009
Tips for a great answer:
Jun 06, 2015 | LG Heating & Cooling
Sep 29, 2013 | LG Heating & Cooling
Jun 12, 2013 | LG Art Cool LA181CNW Split System Air...
Apr 08, 2011 | LG Heating & Cooling
Dec 10, 2010 | Heating & Cooling
Apr 13, 2009 | LG LSC121PMA Split System Air Conditioner
Feb 15, 2009 | LG LSC121PMA Split System Air Conditioner
Jan 14, 2009 | LG LSC121PMA Split System Air Conditioner
37 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: