Question about Heating & Cooling
This is condensation from your a/c running. This is the secondary catch pan which means the primary drain is clogged with algae and not draining, running into the overflow (what you see).
When they plumbed the main drain they should have left a "T" in the pvc line to allow for servicing it. A lot of people will pour a 1/2 cup of clorox into the line every 3 months or so to keep the algae clear. There is probably something more user-friendly at one of the big box stores.
I have a little air tank that I fill with air and disconnect the line and forcefully blow it out. Problem solved.
Posted on Jun 19, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 20, 2015 | Heating & Cooling
Jun 27, 2015 | LG LWHD1800R Wall/Window Air Conditioner
May 13, 2014 | 1994 Buick LeSabre
Jan 02, 2014 | Comfortmaker Heating & Cooling
Jul 12, 2011 | Heating & Cooling
Jun 06, 2011 | GE AEV05LN Air Conditioner
May 12, 2011 | Heating & Cooling
Jun 22, 2010 | Ruud UBHC Air Conditioner
Jun 04, 2010 | Goodman GMS90703BXA Heater
Oct 05, 2008 | Goodman Heating & Cooling
202 people viewed this question
Usually answered in minutes!