Question about Heating & Cooling
Error code 97. Model astg30lfcb - aotg30lftb outdoor unit fan motor error. How to reset
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
16. SYSTEM RESET
a. Turn the ON/OFF switch to OFF position.
b. Simultaneously depress and hold the MODE and ZONE
push-buttons while turning the ON/OFF switch to ON.
FF should appear in the LCD display until the MODE
and ZONE push-buttons are released.
c. When a dip switch is turned on or off after initial configu
ration, a system reset will need to be done before the
Comfort Control CenterTM will recognize the updated selection. Try this. This is for the five button thermostat. Did you check the dip switches to be sure the proper ones are turned on? I need to know which stat you have 4 or 5 button. I have trouble shooting for both.
If you notice reset needs to take place after a dip switch is turned on or off. The dip switches are on the circuit board. You need to drop the lower cover. the dip switches will read in this order #1 heat strip/ #2 zone2/#3zone3/ #4 zone4/#5 furnace/#6 differential/#7stag/#8 gen start. Check this out and be careful. Turn off the stat to change dip switches. On will be toward the description. If you don't have remote start gen set the dip should not be on. If you dont have a Zone 3 the dip should not be on, etc.
Any questions feel free to post back
Thank you for using fixya
Posted on Mar 26, 2009
Hi! You need to check pump filter. It could be jammed with a coin or hair clip. Now take the machine outside and empty it then lay it on its side and you can access the pump. Take it off, stand up the machine and pour hot water into the soap draw and check water should run out of bottom freely taking any fluff or bits with it. Now take apart the pump and clean it and dry all components before re-assembly. If the machine still doesn?t work then you need to replace the pump. Please do rate this solution as FixYa and revert for further assistance. Thanks Rylee
Posted on Jun 13, 2009
SOURCE: LG split (3 indoor) LMU360CE
The LED #2 is only flashing while in disconnection or short in Thermistor (3 sec off / 0.5 sec on). If you want to change it, note: this is not an easy job to do! You will need to remove the top panel, then remove the control paneland then the front panel to gain access to the thermistor. The part isnot available to the public and requires an authorized service techfrom LG to take care of this problem. You will need a special tool toremove the front door seal spring clamp.
But you can call customer service @ 800 243 000 and see if theycan transfer you over to parts. Just give them the model and serial #and see if they would be willing to sell you the thermistor part. Youwill also need the door seal spring clamp removal tool to make the jobeasier.
Posted on Aug 02, 2009
5 flashing is ' compressor drive' and check the high pressure, condenser fan motor capacitor for proper running
Posted on May 21, 2010
Tips for a great answer:
Dec 29, 2016 | Fujitsu Heating & Cooling
Nov 17, 2016 | Fujitsu Heating & Cooling
May 16, 2015 | Fujitsu 36CS Air Conditioner
Jan 09, 2015 | Fujitsu 15RLS2 Halcyon Wall Heat Pump Air...
Apr 07, 2014 | Fujitsu Heating & Cooling
Nov 03, 2013 | Fujitsu ASU12RLS2 Wall Mounted Indoor Unit...
Jul 30, 2013 | Fujitsu 24C1 Air Conditioner
Jan 24, 2011 | Fujitsu Heating & Cooling
Dec 13, 2008 | Fujitsu 18C1 Air Conditioner
May 17, 2008 | Fujitsu 24C1 Air Conditioner
903 people viewed this question
Usually answered in minutes!