Question about Goodman CLQ36AR49 Air Conditioner
I changed out r22 condenser unit , I installed a used working trane Xl-13 . I have 150 psi on high side port and little to zero pressure on low side test port. Is it possible that trash could be against low side service valve. Or incompatibility with air handler and condenser unit? It was around 70 degrees outside
Posted by Anonymous on
I would suspect the valve on suction side not open. if the other system failed on a burn out you could have a blocked dryer or orfice at coil.
Posted on Aug 09, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I am working on a
It sounds like you are low on charge. I think you have a thermostatic expansion valve and you need to check the subcooling, you should have 12 to 15 degrees at 95. At 95 degrees your head should be about 280# for a 12 or 13 SEER unit or higher depending on the effeciency. At 78 to 80 degrees indoor depending on the humidity, that is normal. The valve will open to try to fully feed your indoor coil and it sounds like your head pressure is to low to force enough refrigerant thru the coil.
Posted on Aug 18, 2010
SOURCE: I had my GSC13048AG aicr
I believe He is talking about the suction pressure, not head pressure which runs much higher, he's likely correct but this symptom could be due to several things, discuss it thoroughly with your service provider
Posted on Jul 26, 2011
SOURCE: hello, my HVAC is constantly
I'm new at this and I can't tell how old the post is but I'll contribute anyway.
You probably have fixed the problem by now. I wonder what part of the system is freezing up. I don't have a lot of experience but I know you can get frost where there is a restriction in the freon. If the freon line filter near the outside unit has frost on the house side the filter is partially plugged. I have also seen fost on the evaporator (attic "A" coil) when there is a shortage of return air flow. You could have a plugged filter or colapsed return duct, or even an "A" coil with a lot of dust covering and plugging the fins. I guess restrictions in your room air supply registers could cause the problem too. Maybe you have most of the vents closed off to save energy. Just some possibilities.
Posted on Oct 31, 2012
Tips for a great answer:
Apr 20, 2014 | Goodman CKL42AR42 Air Conditioner
Sep 26, 2011 | Heating & Cooling
May 02, 2011 | Heating & Cooling
Apr 20, 2011 | Heating & Cooling
Jul 22, 2010 | Whirlwind FH-778 Air Conditioner
May 10, 2010 | Heating & Cooling
Jul 03, 2009 | Heating & Cooling
May 10, 2009 | Heating & Cooling
Apr 25, 2009 | Heating & Cooling
59 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: