Question about Heating & Cooling
I have a Brivis ME20e and cannot fint info on changing the heating fan speed. my unit just pushes a tiny bit of air and I want to know if it can be adjusted. thanks
All u do is turn the wall controller to the off position. then press the clock button then hold buttons 2 and 4 down at the same time. let it load for 10 sec then turn the knob all the way untill it sais 1500 that is max fan speed then push the off on button to exit it. dont adjust any other values in here tho just the first one
Posted on May 23, 2014
Testimonial: "Thanks Chris. This seems to have made a difference!"
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
On the unit outside there is a button that says "push man. pull auto" if it is set to push man then the fan will go constantly.
Posted on Nov 08, 2009
SOURCE: how to fix error 35
Error 35hi means faulty heating/temperature sensor ( thermistor) in the ducting that needs to be replaced by a Brivis technician. A technician will cost call out (including all labour) + the cost of the part.---------------- The Thermister is in the supply air duct generally about 1-2m from the heater, with wire going back to heater which plugs into the underside of the gray control box. ----------- To get the part and replace it yourself.Its time consuming and it requires proper fitting and proper connection. To order the part, click the link below:--- http://www.brivis.com.au/content.cfm?content=97 ------------- To call brivis technician to replace the part.Please click the link below:---- http://www.brivis.com.au/content.cfm?content=37 ----------- This should help.Thanks.Helpmech.'
Posted on Apr 14, 2011
Tips for a great answer:
May 26, 2014 | Heating & Cooling
Jul 26, 2013 | Cars & Trucks
Sep 05, 2010 | Heating & Cooling
Jul 12, 2010 | Heating & Cooling
May 17, 2010 | Heating & Cooling
Apr 30, 2010 | Heating & Cooling
Sep 22, 2009 | Heating & Cooling
Jun 11, 2009 | Heating & Cooling
May 12, 2009 | Heating & Cooling
Jul 29, 2008 | Heating & Cooling
112 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: