Question about Dehumidifiers
Only two wires and two screws. Shut off the furnace disconnect switch before doing anything. Then Pull off the cover and I do mean pull off. Then undo the two screws remembering what terminal they go to. Remove the screws from the back plate and let the wires fall through the back plate as you pull it off the wall or duct. Put the new back plate in place with the wires pulled thought. Install the screws I the same place as the old ones. Re attach the wires into the same labeled terminals as the old one. Put the new cover on. Turn on the furnace disconnect switch and away you go. To check operation all you need to do is, turn the knob on the humidifier control and listen for the solenoid to open and water to flow to the humidifier. If nothing happens then you need to check for power to the humidistat. Should be 24v. If no power then you need to check the source.
Posted on Apr 19, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 01, 2017 | Dehumidifiers
Sep 27, 2015 | Dehumidifiers
Feb 28, 2015 | Dehumidifiers
Jul 27, 2011 | Danby DDR583R Dehumidifier
Jul 17, 2010 | GE AHG40LJ Dehumidifier
Jan 28, 2010 | Kenmore 54501 Dehumidifier
Dec 30, 2009 | LG Dehumidifiers
Jun 13, 2007 | Kenmore 53701 Dehumidifier
Jan 11, 2007 | Danby DDR401 Dehumidifier
65 people viewed this question
Usually answered in minutes!