Water to hot for gas boiler boiler gos off
It could be dyslexia, but I think you want to know what may be wrong with your boiler in this case!
This is a VERY old design. The diaphragm is on the water section, this operates a switch to turn ON the pump, and a further device causes the diverter valve to divert boiler water from CH duty to HW duty.
From your description it appears that the boiler is shutting down on internal boiler water temperature (too high), your 'briefly too hot' HW symptom may be caused either by the boiler side of the secondary heat exchanger being blocked/caked in sludge, OR the DHW side of it being scaled. Either way a new or replacement (descaled) secondary heat exchanger MAY inprove things. It's not easy on these old clunk-pots, and EVERY disturbed seal will subsequently leak, so get a good supply of o-rings and fibre seals before you start ("you" being the competant fitter you employ)
Dec 20, 2012 |