Question about Heating & Cooling
Sounds like the ignition is not working, you should probably get a new unit, or get a new ignition module. Depending on price of new module and ability to change it. Or maybe your just out of fuel.
Posted on Apr 17, 2014
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Ok, you either have a inducer fan issue or a pressure switch issue or a plugged vent pipe. The inducer turns on to establish a draft for the exhaust. If it is not working you will get this error code. If the pressure switch does not sense pressure caused by the inducer, it will give this code. If either the intake pipe or exhaust pipe is blocked (even y just a little) it will give you the same error code. If the condensate hose or receptical is plugged, again it will give you this error code. Good Luck!
Posted on Oct 21, 2008
Sounds like you may have a weak or bad flame sensor. If the circuit board does not sense a good flame it will not light the burners. Also if your furnace is 5 yrs or newer it should give you a fault on circuit board in the form of a blinking or a code itself.
Posted on Feb 16, 2009
SOURCE: gas wont ignite
unless you are well trained in troubleshooting you need a pro .carrier furnastys are overly complex you should call carrier dealer if you want the shortest route to a workin system
Posted on Feb 26, 2009
Make sure that the switch on the gas valve is in the on position. If it is and the gas valves coming into the furnace are open, you probably have a bad gas valve.
Posted on Oct 04, 2009
Tips for a great answer:
Dec 05, 2017 | Heating & Cooling
May 07, 2017 | Coleman Propane Forced Air Heater...
Apr 19, 2011 | Heating & Cooling
Dec 11, 2010 | Honeywell L4064B2236 Fan/Limit Control...
Nov 14, 2010 | Goodman GMS90703BXA Heater
Nov 01, 2010 | Heating & Cooling
Oct 31, 2009 | Dayton Gas Furnace Heater
Nov 17, 2008 | Coleman Propane Forced Air Heater...
May 20, 2018 | Coleman Heating & Cooling
76 people viewed this question
Usually answered in minutes!