Question about Goodman Heating & Cooling
Posted by Anonymous on
Older standard efficiency furnaces have a thermocouple. mid and high efficency models do not. they are electronic ignition with a hot surface igniter
Posted on Nov 25, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Make sure all the wire connections are good and tight. Next lift off the cover and look for a little thermal disc mounted up by top of the heat exchanger. Most have a re-set button but not all. If you have this ,by-pass it ,see if that solves the problem, if so it may be defective, or doing its job and you have a venting problem. If you don't have this and have changed the thermocouple (was it a copper tube with a fitting that screwed into the gas valve, or did it have 2 wires, that is a pilot generator, kind of same thing) make sure the probe is set correct, with the pilot flame heating the top 1/3rd of the probe. The only thing left is the gas valve.
Posted on Dec 25, 2007
I had the same problem with a Coleman. The problem is the blower relay. You can find this at http://mobilehomerepair.com
Posted on Oct 21, 2008
SOURCE: thermocouple replacement
Maybe you need to approach it differently. Why do you assume you have a bad thermocouple each time? If its because the whole flame goes out and you have to relite it, a lot of things can cause that.
1 ohm out a new thermocouple and record the ohms reading (read tween the center LEAD looking area on the end going into the gas valve and the outer shell (copper colored cover) If its a MV type controls it will have 2 wire ends. With the flame running now check the MV-DC on the same area, as the resistance. Yes you will need 2 hands extra for holding the flame on. It wont stay on without being hooked up. Typically you need 400MV for a thermocouple and 600 is the stahdardf output on a generator with wire leads depending on which you have. If your below these ranges You need to blow out the piulot area with compressed air and retry it. You should get an increase in the milli volts after cleaning because now the flame will hit the pilot or thermocouple or generator as designed and dust was causing it to be lazy and not get enough voltage back to the gas valve to stay on.
Now this is assuming you have the correct pilot orfice and its not too small like with an LP orfice installed on a NG system. The pressures are differant and the hole is way smaller on LP.
This is a really common problem with multi changeouts of thermocouples. Dusty Pilot burners. y policy has always been to blow it out first after observing the type and kind of flame. Then reexamine it after cleaning it out.
If this helps you please rate me as high as you can. If I have not given you enough information please post back so I can better aquaint myself with you problem. Good Luck!
Posted on Mar 23, 2009
that sensor as you call it is a thermacouple it produces a small current which lets the gas valve know it is ok to open . if the pilot is not clean and correct it will not let main valve open. if your pilot is good then you have bad gas valve. you may have low gas pressure this can also do what you are describing
Posted on Apr 07, 2009
Tips for a great answer:
Dec 20, 2016 | Heating & Cooling
Nov 02, 2015 | Heating & Cooling
Oct 29, 2015 | Williams Heating & Cooling
Feb 11, 2015 | Cozy Heating & Cooling
Oct 07, 2014 | Coleman 7990-319p Evcon Gas Furnace...
Dec 09, 2013 | Heating & Cooling
Oct 15, 2013 | Heating & Cooling
Dec 20, 2010 | Heating & Cooling
Oct 31, 2009 | Dayton Gas Furnace Heater
Sep 16, 2009 | Coleman Propane Forced Air Heater...
66 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: