Question about Leviton Electrical Supplies
On the combination Two Switches #5224 do I break the tab to permit it to operate two units separately. Are the white wires attached?
No need to break the tab... that' on the power IN side of the switch..
You only need one power in (in most cases).
The power outs are separated already.. one goes to your first load and the other will go to the second.
The white wires are your common and are hooked together with the other whites in the box... don't hook them to the switch.
Hope this get's ya all connected... let me know if you need more assistance.
Posted on Jun 19, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 10, 2014 | Leviton White Double Wall Light Switch...
May 07, 2014 | Leviton 5224-2 Wall Duplex Switch
Feb 19, 2011 | Leviton 002-1754-W Dual Rocker Switches
Dec 11, 2010 | Leviton 5224-2 Wall Duplex Switch
Oct 26, 2010 | Leviton COMBINATION SINGLE POLE TOGGLE...
Nov 04, 2009 | Electrical Supplies
Jun 15, 2009 | 1989 Pontiac Grand Prix
Jan 05, 2009 | AEG B1180-4 Electric Single Oven
845 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: