Question about Rinnai Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Rinnai RHFE 1001FA
i have a rinnai rhfe 1001fa heater and when its real cold sometimes it will shut down all the lights go out and i have to shut it off then turn it back on and sometimes it still wont start and i will leave it of for a day or two then try it and it will work it seems to act up more when its colder i am running it this fall so far no problems this unit is around a 1994 or so and has not given any trouble till this started last winter
Posted on Sep 19, 2007
SOURCE: Rinnai RHFE 1004F Error code 49
A 49 error code is caused by the pressure switch either not proving or a bad component. Check the hose attached from the plastic elbow located behind the heater going to a small square pressure switch found inside the heater. It may have come loose or a mouse may have taken a bite out of it. Also while you are behind the heater, pull off the hose that looks like a vacuum cleaner hose and run the heater with it unattached. If it runs, you have a blockage in the vent. If not, take a flashlight and go outside to the vent. Look down the center pipe for any obstructions. If it still does not work, you may need a new pressure switch.
While the front panel is off the heater, cycle the heater to attempt a start. You want to make sure the blower turns. If it does not, check the wire connections to it. You may be looking at a bad blower. If it is turning but still does not start, we are looking at a bad pressure switch.
Let me know what you find, I may have a switch or blower motor that you can purchase.
Posted on Nov 01, 2007
SOURCE: Rinnai 1004 F Error Code 11
Code 11 is that the unit is trying to light but does not sense a flame after 5 seconds. Usually means you have run out of gas if you are bottled gas. Check your bottles are turned on if you are on LPG, you might need to change over manually. Have you anything else on gas?
Posted on Jul 21, 2010
SOURCE: our RHFE-263FA gives an 11
Hi, well this happens when the, thermistor or thermostat is faulty, you need to use these manuals supplied, at the above links.
Posted on Nov 13, 2010
Tips for a great answer:
Oct 13, 2010 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Sep 17, 2010 | Rinnai RHFE-431FAIII 16,700 BTU Direct...
Jul 01, 2010 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
May 13, 2010 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Oct 04, 2008 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Nov 06, 2007 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
20 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: