Question about Heating & Cooling
When Cool cycle is selected, Cycle works ok, the issue is that never stop and I can see the room temperature, 24 volts is ok, equpment is working ok.
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: thermostat ?
The Air conditioner are good only the adjustment of thermostat are the problem, select the thermostat in lower #3 you observe the thermostat will off in such time temperature reach to #3 If you full adjustment the compressor will not off.
In fan selector the compressor will autamatic off because no connection attached fan only .
Posted on Jan 08, 2008
if your problem has existed since the begining of installment it could be a return/ thermostat placement problem. if the return is to close to any supply vents it will run like that and your thhermostat will read like that
Posted on Apr 25, 2008
SOURCE: thermostat ?
I'm thinking the bi-metal is working, that's why you can hear a click, but the contacts are welded together. The bi-metal doesn't have enough strength to break the weld. Time for a new thermostat.
Posted on Jul 23, 2008
check with the company u brought it from and check if you have not put the correct conector to the right temals on the back of the switch.
Posted on Jun 09, 2009
SOURCE: Blown Transformer heat pump
blown transformers are usually from a low voltage short the first thing i would do is wire a automotive or resetable 3amp fuse in line with the transformer so you dont blow transformer after transformer the wire coming off the transformer that say 24v take that wire a couple of inches down and cut it and install the fuse in series there
now you can go through your low voltage wires one by one and test them unhook all the wires to your outdoor condenser at your indoor unit(furnace or airhandler) and try turning it to cool now if you blow the fuse the short is between the tstat and the indoor unit if the fuse is still good leave it on cool and hook up one wire at a time to your outdoor unit starting with R a lot of times your contactor or your defrost board will short out on you also look for pinches in wires wires with cracks in the insulation and wires touching metal this situation can be a real pain sometimes i would recommend calling a hvac company if you start to get stumped
hope this will help you
Posted on Jul 26, 2009
Tips for a great answer:
Jan 11, 2015 | Robertshaw 9600 Heat / Cool Digital...
Nov 06, 2013 | Robertshaw Thermostat 8406-1 Digital...
Oct 06, 2013 | Robertshaw 9500 Digital Non-Programmable...
Jun 02, 2012 | Heating & Cooling
Jun 16, 2010 | GE (PSS26MSRSS) Side by Side Refrigerator
Jun 09, 2009 | Heating & Cooling
Jan 05, 2008 | Kenmore 73089 Air Conditioner
35 people viewed this question
Usually answered in minutes!