Question about Hardware & Accessories
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
the problem is not necessarily with the timer. it seems you have more than ample time and time allocations to perform a complete defrost. most walk ins should have roughly 25-40 minutes of defrost every 4 to 8 hours. if you defrost with a heating element, you may have a problem with the strength of the element,or the element may be pulled away from the coil. you could also have a problem with the defrost thermostat(allowing the defrost to terminate prematurely)
Posted on Jun 17, 2009
Tips for a great answer:
May 16, 2014 | Paragon 4001-0G Defrost Timer
May 07, 2014 | Paragon 8145-20 Defrost Timer
Jun 24, 2013 | Paragon Hardware & Accessories
Jun 19, 2012 | Paragon 4001-0G Defrost Timer
Oct 07, 2011 | Paragon 8145-20 Defrost Timer
Aug 14, 2011 | Paragon 8145-20 Defrost Timer
Aug 07, 2011 | Paragon 8145-20 Defrost Timer
Jan 12, 2011 | Paragon 8025-00 Enclosed Indoor 24 Hour...
Dec 29, 2010 | Paragon GENERIC REPLACMENT MECHANISM 110V...
Dec 21, 2010 | Paragon 8145-20 Defrost Timer
Aug 18, 2017 | Hardware & Accessories
38 people viewed this question
Usually answered in minutes!